Gent VIG-BNG-RW Bacnet Gateway Assembly for Vigilon & Compact with Controls & Command Builds
The BACNET-GW-3 provides an interface between NOTIFIER’s fire panel network (either the standard or the high-speed version) and a network using the BACnet/IP communication protocol.
BACnet protocol is an American National Standard (ANSI/ASHRAE 135-1995). With the Gateway inter- face, devices on NFN fire alarm control panels are represented as BACnet objects to the BACnet client.
The user subscribes to Event Notification objects per FACP, and the BACnet device receives events from objects on the FACP as a result of this subscription.
The BACNET-GW-3 can be connected to a stand-alone ONYX® panel (9th edition) with an available network port, or it can be connected to via the network port on any net- work control module.
Connected to each BAC- NET-GW-3 can support a maximum of 14 other nodes or 15,000 objects. Multiple BACNET-GW-3s can be used to interface with larger networks
The Vigilon BACnet Gateway (VIG-BNG) provides an interface between a computer network and GENT EN54 Vigilon fire detection and alarm system, using BACnet communication protocol.